The PAC 512 can control all aspects of two secure doors, with up to two card readers installed as entry and exit readers on each door. This enables the PAC 512 to support a door strike to lock and unlock a door and a door contact to detect the door positions.
A programmed auxiliary input is put on each door which can be used for alarm system integration, and an auxiliary output that enables a buzzer or strobe when security is breached or a door is left open. Each PAC 512 controller has a tamper input, this enables monitoring of cabinet doors, and an override input that can release both doors.
The PAC 512 can be used standalone with optional IP connectivity or as part of a system controlled by the PAC 500.
|Dimensions||H: 125mm W: 180mm x D:60mm|
|Weight||0.4 Kg nominal|
|Temperature||Operating: -10ºC to 55ºC (14ºf to +130ºf) Storage: -25ºC to +80ºC (-13ºf to 176ºf)|
|Humidity||0 to 85% RHNC|
|Door Configuration||Each door supports up to 2 Oneprox, PAC or KeyPAC Readers, 1 Wiegand output or 1 Magstripe output reader|
|Supported Reader Protocol||PAC, Wiegand and Magstripe|
|Inputs||Door contact, RTE, and programmable auxiliary input|
|Outputs||5-AMP single pole double throw lock relay and alarm relay|
|Status LED’s||RS-232, RS-485, Door 1, Door 2 and system status, Ethernet transmit and receive status|
|Memory Backup||3V rechargeable lithium cell (monitored and status reported) – 6 months memory retention when not powered|
|Communication Ports||RS-232 (57,6K bps), RS-485 (57,6K bps)|
|Wiring Requirements||RS485 – CAT5 up to 1000m, 3000ft total cable or 7/0mm², 24 AWG Alarm Cable up to 500m, 1500ft total cable. RS232 – 7/0mm², 24 AWG up to 7.6m, 25ft max length|
|Module Power||10,5 VDC to 28 VDC @ 220 mA|