You are using an outdated browser. Please upgrade your browser to improve your experience.
CAN WE HELP?Enter your details and we’ll be in touch.
|DC||Door Contact (Grade 2)|
|PIR||Passive Infra Red Movement Detector (Grade 2)|
|DT||Dual Technology Movement Detector (Grade 2)|
|BG||Break Glass Detector|
For a Grade 2 System, Anti-mask detectors are not a requirement.
DD243 still applies regarding overlapping coverage, so PIR coverage must not overlap.
It is acceptable for DT coverage to overlap with PIR or other DT’s.
A 45 second maximum entry timer is permitted, with a further fixed 30 second warning period, before Entry (unconfirmed) Alarm is notified to the ARC.
Grade 2 Systems would normally provide an ATS with at least 1 self powered audible WD (SAB/SCB), or 2 remotely powered WD’s.
Grade 2 Systems require 12 hours standby when using a ‘Type A’ PS.
|ACE||Ancillary Control Equipment||(eg Exit Terminator Switch)|
|PACE||Portable Ancillary Control Equipment||(eg Remote Keyfob)|
|CIE||Control and Indicating Equipment||(eg Alarm Panel)|
|WD||Warning Device||(eg Bell Box, Sounders, Strobes)|
|ATS||Alarm Transmission System||(Signalling System)|
|ARC||Alarm Receiving Centre||(Monitoring Station)|
|PS||Power Supply||(Power Supply for I & HAS)|